There are two possible reasons for the condensation buildup. First, the damper on the outside exhaust hood is either stuck open or missing. This allows freezing cold air into the duct, which chills the ceiling below. The second possibility is that cold air is coming into the ceiling area through the opening in the outside wall between the exhaust duct and the wall. You should seal this with foam in a can, not just fiberglass. On a brick veneer wall, the exhaust duct must be watertight to the brick and airtight to the sheathing behind the brick. Also ensure that it slopes to the outside to drain any condensation outdoors.
You are here: / / / Exhaust-Fan Condensation
More From Reader’s Digest
- Chimney-Wall Condensation I changed my standard brick fireplace to a gas one. I installed a liner on the inside of the chimney, but I am finding condensation between the liner and the chimney wall. It does not […] Posted in Home Improvement
- Installing Insulation I have an old brick house that has been stripped of all walls except the outside brick wall and the open stud wall. I want to seal all air holes from the inside and install insulation in […] Posted in Home Improvement
- Furnace Filters-2 My house was built in 1954 with brick exterior walls and plaster interior walls. The house is extremely cold in the winter, particularly near the plaster walls. I have added insulation to […] Posted in Home Improvement